A-Team Leak Detection was commissioned to source a leak causing damage to the utility floor at a residential property in Co. Wicklow. The following water networks were tested;
Hot domestic supply
Cold domestic supply
Water main supply
Waste water pipe network
During our investigation we tested all the pipe networks at the property with the aid of tracer gas, acoustic equipment and thermal imaging. All networks past our pressure tests except for the water-main pipe network. We had a drop in pressure of 0.5 bar over 2 hours.
We were able to identify a leaking pipe under the utility floor. We fixed the pipe and retested to network to ensure their were no more additional leaks on the system.