When recommissioning the heating system the circulating pump was coming on intermittently. This is due to ware&tare and should be address immediately to insure efficient and reliable heating throughout the building. This work can be quoted for and carried about by us straight away if you wish.
The boiler and time controls were functioning as they should.
On inspection the remaining gun barrel piping in the ground is in excellent condition and shouldn’t be of any concern.
The holes in the entrance/lobby area have been back filled with rubble. Pat is going to reinstate the concrete and make good the tiles.
The heating system will need to be monitored over the next week or so as there will be pockets of tracer gas in the pipework that will need to be vented out and the system re- pressurised. Pat is going to carry out these works, should he have an issue he will contact us for help and advice.
Various videos/pictures were taken of the leak and will be kept on file should you need them for future reference.